Balancing Act: Weighing the Pros and Cons of Lead-Acid Battery TechnologyNOV.28,2023
Advancements in Lead-Acid Battery Design: Efficiency and PerformanceNOV.24,2023
Understanding the Discharge Characteristics of Lead-Acid BatteriesNOV.23,2023
The Future of Lead-Acid Innovations: Trends Shaping the IndustryNOV.22,2023
Start-Stop Battery Maintenance Tips: Prolonging Lifespan and Ensuring ReliabilityNOV.17,2023
The Superior Performance of Lead-Acid Batteries: A More Reliable ChoiceNOV.17,2023
Lead Acid Batteries: Leaders in Multifunctional PerformanceNOV.16,2023
Innovations in Start-Stop Battery Technology: What Lies Ahead?NOV.10,2023
Lead Acid Batteries: Widely Used and Essential in Any FieldNOV.09,2023
Economic and Environmental Benefits of Start-Stop Battery Equipped VehiclesNOV.08,2023
Spaceflight Power Supply Co., Ltd.
Add: Weimin High-Tech Development Area, Fusha, Zhongshan, Guangdong Province, China
With the rapid development of information and computer network in recent years, the smooth operation of data center cannot be separated from the guarantee of UPS system. At present, in the construction of data centers in China, the UPS system mostly uses valve regulated sealed lead-acid batteries（VRLA） as backup emergency power. Among the factors affecting UPS stability and reliability, battery leakage is the most serious potential danger.
Preventive measures for leakage of high power lead-acid batteries
In general, data center users to prevent battery leakage caused by short circuit hazards, mainly take the following measures.
Data centers to install the insulation pad is the most simple and effective to prevent a method of high power lead-acid battery short circuit, its general placed in the middle of the bearing beam of the battery and battery support, through the way to increase the insulation pad at the bottom of the battery, the battery leakage of the electrolyte fluid accumulation in the insulating mat to prevent battery leakage flow of corrosive liquid and the battery at the bottom of the conduction cause electrical short circuit between metal frame, installation diagram as the picture:
Each layer of the battery anti-seismic steel frame is lined with plastic insulation jacket to cover all the metal bearing beam in contact with the battery shell, as shown in picture:
Its function is to separate the battery from the metal battery frame to prevent the leakage of corrosive liquid from conducting the battery and the battery, resulting in electrical short circuit. The insulation sheath is generally designed to be u-shaped and stuck to the battery load-bearing beam. And it doesn’t affect the ventilation and heat dissipation of the upper and lower layers of the battery.
In order to avoid the corrosive liquid leaking from the battery affecting other racks or batteries, a tray is designed at the bottom of the battery to hold the entire battery completely. The length and width of the tray are slightly larger than the length and width of the battery. The acid leaking from the battery can flow into the leak-proof liquid tray with the battery tank. Pallet thickness design should have certain strength to support the weight of the battery. Installation diagram of leak-proof tray is shown in picture: